The BA-PFI-GYP is specially designed to be installed on fire rated drywall covered ceilings and walls. Once a sufficient layer of drywall compound is applied to its corner bead flange, it will leave only the door panel visible for a more aesthetic look. Once the installation is complete and the provided springs are hooked to the back of the panel, this door will be self closing and self locking thus meeting fire certification standards. The largest fire rated PFI-GYP doors available for vertical and horizontal installations are respectively: (48’’ x 48’’) and (24’’ x 36’’ or 864 sq inches).
BA-PFI-GYP fire rated access door specifications,
Material: 16 gauge cold rolled steel frame and 20 gauge galvanneal steel door
Insulation: 2" mineral wool
Hinge: Continuous piano hinge
Lock / latch: 2 x Self latching tool-key operated slam latch and/or ring operated slam latch, both included
Inside panel release: Included on all slam latch fire doors
Automatic panel closer: Standard on all doors
Finish: DuPont high quality white powder coat
Packaging: Individually wrapped, 1 per box
For installation in vertical wall assemblies:
Rating 1 1/2 hours. Temperature rise: 250°F (139°C) at 30 mins and 450°F (250°C) at 60 mins. Maximum door size of 48" x 48".
Rating 3 hours. Temperature rise: 400°F at 60 mins. Maximum door size of 48" x 48".
Standards listed: NFPA 252-2003, UL 10(b), UL 555, CAN/ULC S112 M90-R2001, CAN/ULC S104-10.
MEA # 507-06-M
Fire rated by Intertek - Warnock Hersey
Note: This size is not Rated for Horizontal / Ceiling Installation
This access door can contribute directly to a project's ability to achieve LEED certification:
- LEED-NC New Construction & Major Renovations
- LEED for Schools
- LEED-CI Commercial Interiors
- LEED Canada-NC New Construction & Major Renovations
- LEED Canada-CI Commercial Interiors