The BA-PFN-GYP access door is not insulated and can only be used on fire rated walls, specifically those made of drywall. Once a sufficient layer of drywall compound is applied to its corner bead flange it will leave only the door panel visible for a much better finished look. As per UL standards, once the installation is complete and the provided springs installed, this access door will be self closing and self locking. It should not be used in situations where protection against temperature elevation is required. The largest fire rated PFN-GYP door available is: (36’’ x 36’’).
BA-PFN-GYP fire rated access door specifications,
Material: 16 gauge cold rolled steel frame and 20 gauge galvanneal steel door
Hinge: Continuous piano hinge
Lock / latch: Self latching tool-key operated slam latch and/or ring operated slam latch, both included
Inside panel release: Included on all slam latch fire doors
Automatic panel closer: Standard on all doors
Finish: DuPont high quality white powder coat
Packaging: Individually wrapped, 1 per box
For installation in vertical wall assemblies
2 hour fire barrier, rating 1½ hours. Access/Door Frame Assembly (uninsulated) for installation in vertical wall assemblies. Maximum door size of: 36" x 36".
Standards listed: NFPA 252-2003, UL 10b, UL-555, CAN/ULC S112 M90-R2001, CAN/ULC S104-10.
MEA # 507-06-M
Fire rated by Intertek - Warnock Hersey
This access door can contribute directly to a project's ability to achieve LEED certification:
- LEED-NC New Construction & Major Renovations
- LEED for Schools
- LEED-CI Commercial Interiors
- LEED Canada-NC New Construction & Major Renovations
- LEED Canada-CI Commercial Interiors